How to better use the filter cartridge dust collector
Filter barrel type dust collector is a kind of equipment with very good dust removal effect. With the characteristics of good filtering effect, small shape and large filtering area, it is deeply loved by people. So, how to better use the filter barrel dust collector? Let's learn about it!
Start the procedure of cartridge dust remover, turn on the power supply of the electrical control box first, and the power indicator light is on; start the compressed air source to inflate the air bag, turn on the injection system of the electric control cabinet, start the induced draft fan of the dust removal system, adjust the control panel of the control instrument, and determine the dust cleaning interval (i.e. ash cleaning cycle) according to the dust amount. To close the program, first press the fan stop button to turn off the power supply of the ash cleaning program, turn off the air source, and then turn off the power supply.
After the power supply of the pulse controller of the cartridge dust collector is turned on, the control system is in automatic operation state. The parameters of the pulse controller inside the electrical control box have been set in the factory, and then can be adjusted according to the field conditions. The ash cleaning pressure of compressed air should be controlled within 0.4MPa ~ 0.6MPa, generally 0.4MPa.
Dust in ash hopper shall be cleaned regularly during operation and after shutdown. When the equipment is equipped with an electric dust discharge valve (optional part), when the equipment is running, the electric dust discharge valve can be opened automatically or manually to clear the dust, so that the dust in the ash hopper can fall into the ash storage bucket or dust bag; when the equipment is equipped with manual gate valve (standard accessories) or manual butterfly valve (optional part), the manual gate valve or manual butterfly valve can only be opened for unloading after the dust removal equipment stops running Grey work.
When the equipment runs for a period of time, the resistance of dust removal system will increase, and the value of differential pressure gauge (option) will increase accordingly. After continuous injection for a long time, the value of differential pressure gauge does not decrease, and when the value of differential pressure gauge is out of the set value of instrument, there will be corresponding alarm and prompt. At this time, it should be considered whether the filter element has been worn and the filter element needs to be replaced.